Two gang electrical box for use with nonmetallic sheathed cable
Catalog #: P-442
Height: 3-3/4 in.
Width: 4 in.
Depth: 3-9/16 in.
Volume: 43.5 cu. in.
Type of Installation: New Work
Number of Gangs: 2
Carton Quantity: 48
Carton Weight: 17 lb.
U.S. Patent No. 6,365,831 B1
Country of Origin: United States of America
Molded-in splined device holes, offset gauge marks, leveling ribs
New work residential construction 2 HR fire resistive walls
ANSI / UL 514C: File No. E30594
Fire Test of Building Construction Materials
ANSI / UL 263: File No. CEYY.R9379 (Category / File No.)
Note: Products must also be certified to: ANSI / UL 514C
Fire Resistance Classification in Wall Assemblies 2-Hours or less
Shall be separated by a horizontal distance of not less than 24 inches
Note: For more details please refer to the UL fire resistive directory and Allied Moulded’s CEYY.9379 (Outlet boxes and fittings classified for fire resistance)
Angled mid nails
Carbon steel fasteners